Abingdon, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Abingdon, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Abingdon, MD
Spickler - Abingdon, MD
Quick and courteous! Fixed the issue very quickly, and explained everything in detail. Very happy. I can't thank you enough!
On arrival found outside unit not operating,found bad compressor.also Contactor is burnt in addition to ,customer informed me that unit has history of a leak but previous company couldn't find it .checked standing pressure which was slightly low .recommeded leak search .custmer declined repair at this time .
The thermostat displayed no 24volts power from the furnace. I went into the attic and the furnace door had not been latched back correctly and it had separated from the furnace several inches allowing it the door switch to open. I replaced the door making sure it fit and secured correctly. As soon as the furnace door was properly secured the blower began operating. I went to the condenser to make sure it was working.
Spring Pm On 06/17/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter recommended replaced air filter checked condenser unit outdoor checked electrical connections checked compressor capacitor checked pressure and temp zero leaks checked all electrical connections units operating normal at this time.
Upon arrival, stystem cooling properly, working properly, found blower cap and run cap outdoor weak, customer approved work and signed up for service agreement. Replace and working properly now.
FOUND THE REFRIGERATE LEAK ON THE HIGH SIDE SRATOR VALVE. REPAIRED AND CHARGED THE SYSTEM. CHECKED OPERATION.
On arrival found pan full of water and dirty filter. I replaced filter.Measured return and supply and I was only getting 2 degrees differential. I removed wet switch from the pan and I noticed my delta T started to changed. Return 80 and supply 68. I put my gauges on and my super heat was high and sub cool was low. I did I leak search but I wasnâ€™t able to find the leak. Customer want us to comeback and do a nitrogen leak search. Customer stated that we have a credit card on file, we have been charging it for years. Leak search + todayâ€™s trip fee needs to be charge. Custumer want us to comeback on Monday. She will be home all day.
Replace voltage absorption system, voltage distribution system and install a hard start kit.
I replaced the air filter with one provided by the customer. I cleaned the condensate drain line and ran water to flush out any debris and to make sure it drained properly without leaks. Unit cooling with 20+ degree delta temperatures across the evaporator coil. Refrigerant pressures and measurements were normal, no evidence of loss of charge from a leak. I checked the electrical wiring and electrical systems, and found 2 main components at the condenser that need to be replaced. I showed the customer and also recommended adding a hard start kit. The unit is operating normal, with electrical repairs needed to keep the system running.
Replaced Outdoor Fan Motor and module. Power was shut off when I arrived. Removed old mounting and then removed motor from mount and blade from motor. Installed new motor with reused blade and mounting brackets. Verified tight connections and returned power to system. Customers brother came and let me in house to test unit. Ran ac and checked operation. Outdoor fan running normally with compressor. Measured amp draw of both then took temperature readings at both coil. Found normal heat rejection outdoor and normal delta air temp indoor. Unit is operating normal at this time. **Still need to collect balance from customer. Paid me $300 cash as a deposit for part last visit.**
Upon arrival I was told that ac wasnâ€™t blowing cold air and outdoor fan not running. During diagnostics I found compressor running but outdoor fan not. Removed molex plug from motor and found it is getting both 240v and 24v, Motor should be running. Shut off power and ohmed out coil and found no ohms, winding broken. Quoting customer to replace Outdoor fan motor. Customer approved and paid deposit of $300 (cash) so we can order motor. Office please follow up with customer on part arrival. He would like to schedule return trip for Monday after 3pm if possible.
Invoice created to clear up AR
Upon arrival I found thermostat in off position because customer said unit was blowing too much cold air. During diagnostics I called for 10 degrees of heat. Unit was running 2nd stage heat but aux not running. Found AHU fault Ec which states an unmatched aux heater kit. Found Board was setup for 20kw when heater kit in unit is only 10kw. Changed dip switch settings and reset power. Ran aux heat and checked amperage. Ran HeatPump and aux heat together and checked operation. Unit is operating normal at this time.
Replace 40 gallon gas water heater also needs ball valve expansion tank and drain pan customer also wants water heater raised up off the floor dues to flooding issues. Remove nipple on gas line and install shorter nipple to accommodate raising water heater
Install new diverters in upstairs bathrooms
Cutomer approved installation on 3/4â€ PE water main
Tune Up on 12/13/18 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter recommended to replace the air filter Avery 90days also highly recommended to install UV Lights also customer complain about air filter ruck is to hard to access customer need some one come out check it for him unit operating normal at this time.
On arrival removed flame sensor i then installed new flame sensor.tested unit ,unit operating normal
Fall pm on 11/30/18 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters found for unit #1 in attic flame sensor is bad need to be replaced I gave the quote for customer.customer accepted I ordered the part we have to come back to replaced the part Monday @4:00pm we have to call the customer before 30min also we have to collect full amount of the repairs.