Baldwin, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Baldwin, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Baldwin, MD
Yousef is wonderful!!
Bouyoukas - Baldwin, MD
Yousef is an asset to supreme air. Very friendly and helpful. Supreme air is lucky to have him.
Hall - Baldwin, MD
I love Youseff. He is very polite helpful and seems to know his job. The only improvement would be to please turn out lights and close doors and garage doors behind your exit. Marsha Hall
Great service !
Pawluk - Baldwin, MD
Very knowledgable and helpful
Configure the zones correctly with the guidance of Water Furnace technical support. With Water Furnace tech support on the phone, I restored factory defaults to the master stat. I then added 3 zones, configured their priority and size. I set up staging. I set the damper to 2 wire. Once everything was configured correctly I confirmed that the zone board, zone stats and zone dampers were all working properly. The customer and I set up some scheduling, but the customer is adept at modifying the schedule for the zones if changes need to be made. In short, neither myself nor W.F. have any explanation for how these changes were programmed into the master stat. These configurations are permanent and unless intentionally changed will continue to operate as designed. Unit operating normal. All zones are operating normal.
Upon arrival both systems operating, downstairs unit starting to have a hard time due to dirty evaporator coil, suggest cleaning. Upstairs unit also struggling on arrival from dirty filter, replaced filter and operating better. Upon inspection upstairs found return ductwork dirty, suggest cleaning service. Also suggested to customer possibly having whole house done since ductwork has never been clean.
Canâ€™t find discounts
On arrival found clogged drain ,cleaned drains,also found unit #2 ez trap leaking .need to replace it .customer wanted to consider today's visit as one of his mAintenace visit .
On arrival set unit to call for cooling ,checked system ,found system low on refrigerant ,possibility of a leak .customer preferred to add refrigerant.added 2lbs ,system operating normal at this time .
Found coil frozen ,advised customer to turn system off and call office to reschedule
On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned it and checked water pressure,also cleaned evaporator coil and replaced cap,also custMet signed up for membership.unit operating normal
On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked water pressure and raised it,checked filter,blower, coils drains,units are operating normal
On arrival installed the new screw on high pressure switch,tested unit operation.system operating normal
On arrival found unit not operating,found stuck open high pressure switch .customer paid for rush delivery.
Fall pm 12/07/18 on arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced units operating normal at this time.
Found transformer fuse popped . Search for low voltage short and found that it was in the heat pump . Removed cover to heat pump and found dead mice fried on the capacitor and contactor . There is shorts in the wires that I can identify . The electrical components all need to be replaced including fan motor . Compressor pumps but is extremely loud and shakes unit . Could have possible damage . I would recommended replacing unit due to cost of all the repairs . Gave quote to replace all damaged parts .