Bethesda, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Bethesda, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Bethesda, MD
Great Service, Arrived on time and did great work
Michael - Bethesda, MD
Really pleased. They showed up on time and did a very nice job!
Response from Supreme Air:
Michael thank you very much for the great review! We are thrilled to hear you had such a positive experience with Supreme Air. We look forward to assisting you in the future! Have a Supreme day!
Upon arrival customer informed me he would like tune up. Also mentioned that aux heat wasnâ€™t working properly on Geo. During maintenance I found first floor thermostat not working. Non communicating thermostat wired to communicating board, will not function. Quoted customer to replace and he had WiFi 6000 on site. Customer approved quote so I replaced first floor thermostat and removed daughter board. Wired in thermostat to zone panel and checked operation. During test I found damper is not functioning. Zone panel feeding it voltage but damper reopens and flashes fault on Zone Panel. Quoting customer to replace damper actuator. Other than that unit is operating normal at this time. Customer signed up for Maintenece contract.
On arrival found system operating normal but some rooms are colder than others ,spoke to Troy and informed me that Charlie supposed to install dampers on all branch lines .i then looked for dampers but couldn't find them .i then balanced system by closing some registers.charllie needs to install dampers .unit is operating normal at this time
The humidifier was wired to always have 24 volts even if the unit was not operating at all. The reason it was not noticed earlier is because the humidifier cover was put on incorrectly. It is a 700 powered humidifier so the cover has to be closed to allow the wire harnesses to make contact. I wired it correctly and tested the operation in front of the customer. I asked if there were any other issues or concerns and customer sid no other issues. I spoke with customer about a maintenance membership and left a copy of the membership benefits with them. I called Alex to let him know that this was warranty work.
Customer was able to light water heater before my arrival , checked out heater itâ€™s 12 yrs old and should be replaced or serviced , gave estimate customer will call back in to schedule replacement
On arrival found system tripped on water flow ,found pumps not operating due to blown fuse on the board .replaced 10 amp fuse and inspected connections and pumps .units are operating normal at this time.if the pumps blow again we need to replace pumps .units are operating normal
Replace capacitor on package unit and check operations . Also gave quote for broken damper for second floor system. It was getting 27 volts but stuck open and causing a clicking noise. Costumer also complained of a whistling noise and that was caused from dirty filter costumer had spare so replaced it . Both systems are up and running
Schedule Duct Cleaning
Special order toilet replacement
I operated the unit in high fire heat mode. I calculated airflow to be 1,800 cfm. The temperature rise is within comfort range and matches printed data. Gas pressure to the burners was increased from 3.0 to 3.5iwc. I checked the igniter and flame sensor. I checked the electrical wiring and electrical systems, all are within specification. The unit operates normal in heating mode. Customer signed up for a service membership today. The amount the customer paid on the invoice is for the duct cleaning and dryer vent cleaning. I called Donna and she will call the customer to schedule.
Completed boiler maintenance. All wired connections are tight , No leaks in piping , no blockages in flu venting , bled all the radiators, circulator is pulling inline with amps and operating. Costumer has heat pump but it is not on the service contract . I informed him and let him know it would be an additional fee and he said do not worry about it .
Mr. Spector is going to send us the brand ( Koehler Elon gated water closet and numbers to order one piece long gated elongated a water closet. Estimate with be giving after we have information from Mr. Spector
On arrival removed gas valve and installed an other gas valve .,tested unit operation.system operating normal
I recovered the charge. Removed the compressor and filter drier. Replaced both and used dry nitrogen to pressurize the system to check for leaks. It held 250psi. I then flushed the line set with nitrogen. I also put acid away in the new compressor. I pulled into a deep vacuum and charged with 7lbs 10oz of r410a refrigerant. I checked temperature rise and the unit is operating normal.
Upon arrival I was told that heat wasnâ€™t working on main floor. Went to package unit and found no LEDs on display. Also found top floor system had faulted on water flow because systems use the same flow center. Checked voltage and found no low volts. Removed fused disconnect to find 60amp fuse had blown. Replaced with new and tested systems. No additional problems found and units operating normal.