Brookeville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Brookeville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Brookeville, MD
Salnick - Brookeville, MD
Disconnected meter , from outside , capped furnace and water heater gas lines also reconnected copper stove line into pipe installed air gauge and pressurized for inspection , copper gas line will not pass customer insists on hearing it from inspector. Will call in inspection and give new estimate if or when repairs are needed to be done To replace 3/4â€ gas line where itâ€™s leaking above the furnace , will install a 3 port manifold on wall and use gas tite pipe for furnace and water heater gas feed lines , will then re pressurize system to test for further leaks will also need to tie the stove into the main gas line to test whole house together per the inspector
Upon arrival I was shown melted disconnect in attic. Gave customer quote to replace and he approved. Customer also spoke to Alex about warranty status and why this wasnâ€™t covered. Replaced attic Non-fused disconnect with new one from truck stock. Cut back all wiring and used clean connections. Once replaced I returned power to the unit and tested HeatPump with Aux heat. Unit pulling 43amps on circuit, breaker rated for 60amps. Continued to run system and inspected other disconnects for packaged geo unit. Found no problems there. Shut off power to attic system and checked wiring connections after running for some time. Unit is operating normal.
To replace 3/4â€ gas line where itâ€™s leaking above the furnace , will install a 3 port manifold on wall and use gas tite pipe for furnace and water heater gas feed lines , will then re pressurize system to test for further leaks will also need to tie the stove into the main gas line to test whole house together per the inspector
Will return Tuesday to replace gas lines for furnace and heater and re energize the line for the gas test.
On arrival removed bad flow center ,then installed new one ,then flashed system.units are operating normal
Cust did not answer after multiple calls
On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced recommended need to replace the flow send I gave quote for customer customer he going to call us when his ready unit operating normal at this time.
I replaced the filters with ones provided by the customer. I set both flow rates and checked heat of extraction. I checked the electrical wiring and electrical systems, all are within specification. I recommend adding an intellistart module to the split system cube. Temperature rise is normal on both units. I decreased blower speed with the dip switches on the upstairs air handler to increase temperature rise. I also enabled programming on the upstairs thermostat as it was disabled through the installation setup. I pressurized the ground loop to 65 psi. Both units are operating normal.