Brookeville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Brookeville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Brookeville, MD
Salnick - Brookeville, MD
On arrival found system locked on fp1 15 times .checked system operation.checked EWT AND LWT .omhed fp2 And fp1 sensor. I then replaced fp1 sensor,case number 510969.unit operating normal at this time
When I arrived I talked with customer about codes that came up in the system. When I checked system With AURORA AID TOOL System was normal functioning normal when these calls came up customer reset system customer refuse to pay for diagnostic fee $124 customer was told $89 fee was part of diagnosis the system all I collected today was the $89 dispatch fee customer will give us a call once these calls come up so we can find out what sensor is going bad and we can charge it towards warranty customer says system is 3 to 4 years old I filled out a follow-up form for senior technician to come out if these calls come up in the system again.
On arrival set unit to call for heat and cool .checked system operation.explained to customer how to operate thermostat.unit operating normal .also customer paid in full for duct cleaning .
Estimate for 2 balancing dampers to be installed , and supply vent for basement bathroom, and close off opening in supply trunk.
Tying into existing kitchen lines in concrete floor re-running them in mechanical room and tying them in
Estimate to build heat shield box on wood stove venting to to protect from combustibles
Snaking out kitchen line
Upon arrival I found single switch/receptacle wired to furnace. Shut off breaker but found Surge Protector is bleeding 40volts from basement circuit to furnace circuit when shutting off furnace breaker, customer may want to have electrician take a look or verify if thatâ€™s ok. Replaced receptacle with GFCI. Also installed furnace on off switch. Tested switch and furnace, normal operation. Called for ac and checked operation. Installed uv wrap around lineset. Unit operating normal.
Estimate to replace 4â€ sewer main & 1â€ water main
Snaking Sewer line from House to Street then Camera line to find the cause of back up
Upon arrival I went to furnace and turned on, no voltage at thermostat. Had to rewire safety switches. Changed from parallel and breaking C, to Series and breaking R. Thermostat lit up so I configured settings. Called for ac and blower didnâ€™t run. Opened up CoolCloud app to find system wasnâ€™t configured. Set up system configuration then called for ac. Put gauges on and found unit slightly low in 410A. Added 8oz to system to bring Superheat and subcool to spec. Delta air temp at Evap coil 23 degrees. Ac operating normal. Spoke with Tom who is piping in gas line and he informed me that gas inspector has lock on meter and may not return until mechanical inspection tomorrow. Cannot run gas furnace without gas. Informed office.
Found refrigerate pressures and the sub cooling to be off. Recovered the refrigerate and put the system into a vacuum. Weighted in 5.11lbs of 410A refrigerate. Checked operation. Left with pressures at 115/275 with a sub cooling of 10.6.
5.12.19 gas line for gas heating stove
5.12.19 Tankless water heater
To break up the floor in new bathroom over to the sewer stack , add drains for a shower base , a toilet and a bedai, will also add drain for a new angle lav sink in corner of bathroom , will make connection and will move the water lines over as well will install , new diverter and put cement back when finished , and install water lines and vent for dryer
Disconnected meter , from outside , capped furnace and water heater gas lines also reconnected copper stove line into pipe installed air gauge and pressurized for inspection , copper gas line will not pass customer insists on hearing it from inspector. Will call in inspection and give new estimate if or when repairs are needed to be done To replace 3/4â€ gas line where itâ€™s leaking above the furnace , will install a 3 port manifold on wall and use gas tite pipe for furnace and water heater gas feed lines , will then re pressurize system to test for further leaks will also need to tie the stove into the main gas line to test whole house together per the inspector
Upon arrival I was shown melted disconnect in attic. Gave customer quote to replace and he approved. Customer also spoke to Alex about warranty status and why this wasnâ€™t covered. Replaced attic Non-fused disconnect with new one from truck stock. Cut back all wiring and used clean connections. Once replaced I returned power to the unit and tested HeatPump with Aux heat. Unit pulling 43amps on circuit, breaker rated for 60amps. Continued to run system and inspected other disconnects for packaged geo unit. Found no problems there. Shut off power to attic system and checked wiring connections after running for some time. Unit is operating normal.
To replace 3/4â€ gas line where itâ€™s leaking above the furnace , will install a 3 port manifold on wall and use gas tite pipe for furnace and water heater gas feed lines , will then re pressurize system to test for further leaks will also need to tie the stove into the main gas line to test whole house together per the inspector
Will return Tuesday to replace gas lines for furnace and heater and re energize the line for the gas test.
On arrival removed bad flow center ,then installed new one ,then flashed system.units are operating normal
Cust did not answer after multiple calls
On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced recommended need to replace the flow send I gave quote for customer customer he going to call us when his ready unit operating normal at this time.
I replaced the filters with ones provided by the customer. I set both flow rates and checked heat of extraction. I checked the electrical wiring and electrical systems, all are within specification. I recommend adding an intellistart module to the split system cube. Temperature rise is normal on both units. I decreased blower speed with the dip switches on the upstairs air handler to increase temperature rise. I also enabled programming on the upstairs thermostat as it was disabled through the installation setup. I pressurized the ground loop to 65 psi. Both units are operating normal.