Crownsville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Crownsville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Crownsville, MD
Carol - Crownsville, MD
Yonas was extremely helpful. Answered any questions to my satisfaction.
Response from Supreme Service Today:
Thank you, Carol. We couldn't agree more, Yonas loves helping our customers and never wants to leave them with unanswered questions. We're so glad he was able to answer all of your questions and ensure your satisfaction during his visit. We look forward to sending him to you again for your next HVAC service. Have a supreme day!
When he says my system is working fine, how can I complain?
Mazur - Crownsville, MD
This was a routine semi-annual checkout. And he said everything is mechanically fine. I hope that is the case. He did say that my ducts and the system plenum is very dusty and he is recommending a cleaning and installation of a UV system. He indicated it could affect the life of the system. He could be right, although he didn't offer a detailed explanation about the problem and the value of the fixes. He e-mailed me 3 quotes for different levels of additions to my system, which I will study.
Customer wants his warratied water heater installed. We will go get and install water heater as per customer. We will not supply water heater if payment is needed up front for warranty transfer it will be customers responsiblity to cover said water heater for installation. Monthly charge and install of water heater. collected deposit of 196.83.
Replaced contactor and checked voltage readings ensuring flowing correctly.
Upon arrival found downstairs system operating normal, found contactor burnt, recommend replacing. reusable filter doing poor job at filtering and starting to see signs on dust and microbial growth. Upstairs system coil very dirty with bacterial growth, restricting air flow and forcing system to work harder. Recommend replacing reusable filters with disposable at a minimum but recommend using high quality air filtration and air purification. Indoor coil needs to be cleaned and would recommend also having duct cleaned. Contactor to be covered under manufacturer warranty. Customer would like copy of warranty information from office. Customer would like to have coil cleaned and contactor replaced pending further discount from office.
Upon arrival system running to spec with temps/pressures/amp draws. Found run capacitor for compressor below allowable variance. Rated 40 actual 35.9. Suggest replacing, customer prefers to wait until next year. Customer renewed service agreement, first visit tbd.
COMPLETED THE REMOVAL OF THE HUMIDIFIER.
Spring Pm on 05/08/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter cleanedchecked EWP and LWP also temp checked all other electrical connections unit tested unit operating normal at this time.
Spring Pm On 04/26/19 On arrival set units to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters cleaned checked condenser unit outdoor checked electrical connections checked voltage and amps checked compressor capacitor checked coils units checked all other electrical connections tested units operating normal at this time.
On arrival checked thermostat was calling for cooling. Measured return temperature, supply temperature, amps, voltage, and capacitor. Inspected electrical connections, replaced filter provided by customer, used a vacuum to clean condensate drain line, and blower wheel is clean. I found a pitted contactor, showed it to customer and gave him an stimate. Unit is operating normal at this time.
Fall pm on 01/18/19 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter cleaned recommended UV lights installation unit operating normal at this time.
Fall pm on 01/18/19 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced recommended duct cleaning also uv lights installation unit operating normal at this time.
Hookup kitchen sink drain and valves install kitchen sink faucet hook up ice maker to fridge cut out vent for microwave
Service call on 12/06/18 On arrival set unit to call for heat the furnace running blower blowing cold air checked electrical connections checked voltage and amps found ignitor burnt out also give me error code ps opened checked ps is good fixed the ignitor wires checked electrical connections checked voltage and amps checked supply and return air temp checked filters unit operating normal at this time.