Davidsonville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Davidsonville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Davidsonville, MD
On arrival found system not operating,found gas pressure not set correctly.adjusted gas pressures ,also configured furnace To bring the fan on when heat pump is running .system operating normal
Furnace would fire up when it had set for a while but would not fire back up when it was hot. I checked the pressure being pulled by the inducer and it was under 1.25 unless the furnace had time to cool off. I went through every procedure to rule out causes of low draft pressure, including checking drain tubes to the collector box and the collector box itself. I cut the exhaust pipe to see if the pressure increased and removed the burner compartment door but the draft pressure hardly increased. This lead me to pull as much off to inspect the heat exchanger. Using a scoping camera I was able to go around a bend to find the cause, a cracked heat exchanger in the area with severe discoloration due to overheating. I was able to show the customer the crack. I made the furnace inoperable and turned the gas off. A sales person is coming out tomorrow to quote replacement. Customer does not want this to happen with a new furnace.