Dundalk, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Dundalk, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Dundalk, MD
Good service. Highly recommend
Cynthia - Dundalk, MD
Barbara - Dundalk, MD
Barbara - Dundalk, MD
Can’t wait for this to be done. It’s too hot for me. 5/29/19 today and it won’t be done until 6/3/19. Please hurry. The portable air just isn’t enough or they aren’t working right.
Macin - Dundalk, MD
Always excellent service.
Albert - Dundalk, MD
HAd Supreme Air install a brand new furnace at the residence in Nov. for a total cost of $3,600 in OCt. 2018. Thought that they would be a reasonable resource when the air conditioner needed service. I suggested that the tenant call them, when she noticed that there was so much water in the dish that took the condensate from the air unit. Was shocked to get a bill for $373.00 for such a simple job. Will go elsewhere for future service calls.
Macin - Dundalk, MD
My maintenance service was performed efficiently and my questions answered knowledgeably and with patience.
Response from Supreme Air:
Thank you very much for your kind words! We really appreciate you taking the time to share your experience with Supreme. We look forward to working with you again in the future!
The main ballrooms condenser unit had tripped on high pressure. I applied my refrigerant gauges and reset the pressure switch and had normal operating pressures for r22 refrigerant as well as normal superheat. One of the outdoor fan motors voltage absorption system was not reading any value. I replaced the voltage absorption system and properly dressed the electrical wires within the unit and restored power. I also tightened and secured all cabinet doors on the exterior of the unit. Unit operating normal. Materials: 1) round 5uf run capacitor
Suck out sump pump and fix small leak on clean out
Unit has a bad compressor. Unit uses R22 refrigerate which by 2020 will be no longer available. Suggest putting in a 410A unit.
Installation of Carrier Heat Pump Out door MN# 38MGR Indoor X 2 MN# 40MAQ Total Job $7937.00 Check Deposit $4581.50 Balance due at installation $3355.50
Upon arrival system not operating properly. Outdoor unit off for tstat wiring/pressure code. Inspected tstat wiring found a wire had gotten connected to wrong point. Rewired tstat wire and tested system for every scenario through tstat, system operating properly.
On arrival found system not operating,found thermostat not operating normal,recommended replacing it .customer will call bge to replace thermostat.
On arrival found bad indoor blower motor.unit is 27 years old .customer bought new system
Upon arriving system in top shape. Indoor and outdoor working to specs. Customer had issue connecting mobile device to tstat, reset tstat and resolved issue. Advised protection on condensate line and explained benefit of service plan, customer moving soon and not interested.
Unit was not off ,still frozen .customer only paid $99 .
CHECKED UNIT FOR LEAKS AND OPERATION. DID NOT FIND ANY PROBLEMS AT THIS TIME.
On arrival all system operating temperatures and pressures were good. All electrical connections good. Components clean and in good working order.
On arrival set units to call for cooling measured supply and return air temp I found the air flow no DT I checked air filter is very bad connections I take out the filter tested with out air filter the unit checked electrical connections checked voltage and amps measured supply and return air temp checked evaporator coil is cleaned checked outdoor unit checked psi checked temp checked the freon checked the coil everything is okay the only problem I found the air filter makes air flow problems also thatâ€™s why the line set gate freezing up highly recommended to replace the air filter unit operating normal at this time without air filters. The payment Alex he is dealing with the customer tomorrow 05/08/19 payment not collected.
Estimate to remove leaking radiator in kitchen and install bypass copper pipe in place of radiator collect $325.00 Estimate to remove leaking radiator in kitchen and install bypass copper pipe in place of radiator collect $325.00
On arrival set units to call for cooling it was error code ER3 Low pressure I checked electrical connections checked voltage and amps checked condenser line also the pump the pump is not running bc the receptacle gets feel has reset buttons I reset I suggested replacing now to avoid future problems the unit is coming back working normal checked electrical connections checked voltage and amps measured supply and return air temp checked condenser drain and cleaned checked filter and replaced checked EWP and LWP is good.highly recommended replacing the receptacle 120v also unit needs duct cleaning and hole house surge protection. Unit tested unit operating normal at this time.
On arrival found drain clogged ,cleaned drain ,tested it ,unit is draining properly.please consider this visit us one maintenance visit .customer signed 9 houses to be checked once a year .
Checked wiring and connections. Cleaned drain pan, checked condensate pump. Checked the air filter. Checked unit operations.
Cut out leaking 3/4 copper and galvanized pipe and install new 3/4 m copper on supply and return on existing radiator and remove pipe both supply and return for radiator that was removed in bathroom
Cut out radiator in first floor bath and hard piped with copper tried filling heating system and bleed but could not get preassure to build and air kept getting in lines after searching found pipes under crawl space busted and leaking cust stated she paid roto rooter to fix in feb and was calling them to come back and fix it heat cannot be turned on until busted pipes are repaired
On arrival take out the old flame rods the new one is not the same kind is smaller I have to come back with new flame rod also turn on the water heater checked if has any leak water heater is working fine no leak we have to come back finish the job unit turn off.
Removed second floor radiator , connected piping . Filled boiler and checked operations . Boiler has a shorted flame rod and we need to replace . Put in parts form
Replace the gas valve.
Install 5 ft sleeve on outside of foundation wall and seal outside with cement seal inside hole with cement and silicone inside sleeve installed 1â€ dual check valve
Returned to complete replacement of 1" (PE) Excavated Water Main. Removed bad and replaced with new 1" full port ball valve main shut off and PRV . Inspected all work completed. All work completed to code. Put down Seed & Straw.
Finished install of mater main backfilled left area open for inspection for tomorrow