Dundalk, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Dundalk, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Dundalk, MD
Macin - Dundalk, MD
My maintenance service was performed efficiently and my questions answered knowledgeably and with patience.
Response from Supreme Air:
Thank you very much for your kind words! We really appreciate you taking the time to share your experience with Supreme. We look forward to working with you again in the future!
On arrival set unit to call for heat ,measured supply and return air temp measured voltage and amps inspected electrical connections checked drain cap,safeties ,heat exchanger,coil,exhaust motor little loud ,recommended replacing it .unit operating normal at this time
To replace the copper line over to the angle stop valves , reconnecting to the existing angle stop valves and sink supplies .. - removed broken nipple under hall lav sink , replaced chrome 3/8â€ nipple on cold side and connected to existing angle stop customer had already installed also removed hot side angle stop sealed the threads then reconnected existing angle stop in that side as well. Tested no leaks.
Return air duct was taped to the furnace along the left side but not bolted. I found this was the same for the seam along the evaporator coil. I stripped the tape and secured the flanges wherever they were loose to bring them tight against the furnace. I operated the unit and the noise had completely vanished. I checked temperature rise while I was in front of the unit and found that the blower speed needed to be increased. I also widened the filter access opening to make replacement of the filter much easier. The unit is not making the rattling/ loud vibrating sounds anymore, the filter access is easy to use and the temperature rise is within comfort range, and the unit is operating normal. I spoke with my boss to let them know that this work would be warranties to the installation department.
Fall pm on11/16/18 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced unit operating normal at this time.