Edgewater, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Edgewater, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Edgewater, MD
First Rate Work!
Waddell - Edgewater, MD
Supreme Air is never going to be the cheapest provider, but their work is really excellent, and they stand behind it. Extremely professional and knowledgeable folks. Highly recommend them.
Ron - Edgewater, MD
Their service is always courteous, the technicians are well trained and competent and reliable.
Service call on 02/12/19 On arrival found the thermostat out of the wall tested the old thermostat is broke itâ€™s not operating normal I gave quote for customer T4pro programming thermostat customer accepted replacing the thermostat tested unit operating normal at this time. Also customer sign new SA. Collected $451 C.C
Found system tripped at breaker. Door panel door off saw no burn marks . Checked junction box and found the wire nut had melted and hit the cover causing the breaker to trip . Itâ€™s aluminum wire coming up and copper wire going to the unit . There was no noloc paste used and I think thatâ€™s what caused it to melt . Cut burnt wires and reconnect them . Also used noloc paste on all three connections and checked operations on system .
On arrival found humidifier on the ground, we cleaned it, replace the panel, mounted it back, and sealed it with tape. Customer was not receiving enough heat inside the house due to humidifier was not on the right place. We tested it and checked the unit. System is operating normal.
I operated the unit on low and high heat. I set the manifold gas pressures and checked supply gas pressure. I checked the electrical wiring and electrical systems, all are within specification. I operated the geo unit on second stage heat mode. I set the flow rate and confirmed heat of extraction. I pressurized the ground loop to 65 psi. Unit operating normal.
Had to snake clean out from tub past toilet. Then had to lift toilet to snake main line to out home. Run water and no backup now. Keep an eye on tee under home where water closet set. Tub is running behind water behind water closet , which can cause tub to backup.