Elkton, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Elkton, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Elkton, MD
Great service keep me informed
Kay - Elkton, MD
The whole staff was very accomidaying and he stayed to make sure everything worked with the furnace, hot water heater, and pipes in the sink. Would definitely have them again
Express - Elkton, MD
The Tec was wonderful to work with. Supreme Air is a great company to work with.
Cap off hot and cold lines under kitchen sink and turn water back on to home valve under sink broke and flooded kitchen and basement dust wanted lines capped off due to cabinets being replaced removed water from water heater pan from the leak and restarted gas water heater. Restarted gas furnace also they were turned off to when basement flooded to prevent any more damage
Replace blower wheel, housing and frame. Upon arrival I went to system and removed paneling. Found I do not need to replace blower assembly. Blower was rocking back and forth due to cracking in the frame of unit, similar to unit 1. Went to supply store and picked up reinforced steel. Came back and cut to length and installed bracket underneath blower housing. Secured the bottom of panel and side of panel. Also secured and all sides of the cracks to keep blower from rocking. Put unit back together and tested blower. Blower not rocking or making loud noises. Ran heat and checked operation. Unit operating normal at this time. Office will be sending revised invoice. Waiting on parts for front lobby unit, system shut off.
Unit was turned off from thermostat . made it call for heat and right away could hear the blower motor shaking from inside . Found that blower assembly is shaking the unit and also the blower wheel is grinding against assembly . Need to replace blower assembly and replace belt . Also found rust on heat exchanger but no cracks . Left system with power off on roof , costumer has no heat
On arrival found system locked on limit,found whole unit shaking ,found majority of heat exchanger rusted,.need to replace blower assembly and heat exchanger.recommended not to run unit .