Fallston, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Fallston, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Fallston, MD
S - Fallston, MD
Prompt and great service
Good support for Waterfurnace system...
BBoyz - Fallston, MD
Routine maintenance call for a well-functioning system coincided with a system component failure - it happens. System was left in functioning but less-then-optimal state - which was OK for short time. The next day I needed another visit from the techs to make changes to the temporary set-up - technician was sent very quickly and configured adequate temporary set-up while we waited on new circuit board. Supreme ALMOST loses a star as the wait-time was over a week... (I think they might have forgot about me 😉 ). But when I pinged them - service tech was sent first thing the next morning with the part and did a great job returning my system to 100% operational status. Mistakes happen - it is how they are handled by the service provided that makes the difference. Rapid response - Supreme has been great... though I have received the "...they will be there between 8 and 12..." - that too ALMOST loses a star. They gain it back by sending a picture of the tech before he arrives and actually calling homeowner while tech is still 45 minutes away. Seems simple but not many service providers can manage to do that. Good job Supreme!
Replace hot surface igniter . Checked operations , supply air 127 and return air 72 .
Completed check on system . Found that it is operating properly . Blower motor pulling 2.1 amps , filter is clean , blower wheel is clean , extrications heat pulling 41.9 amps . Supply air with heat pump is 97 degrees and return air 72 . Supply air with aux heat and heat pump is 108 degrees . Costumer has heat .
Replaced warranty intellizone board and checked operations . System and dampers are all working properly .
Upon arrival I found zone panel not always sending voltage to zone 1 (wired to zone 5). Could have something to do with zone 1 not being wired to panel because it is malfunctioning. For now, have zone 1 and 2 constant 24v until we return. Customer preferred that those zones stay open and zones 3 and 4 remain closed.
When we arrived we checked the thermostat and call for heat, we checked water pressure entering and leaving. We checked the temperature entering and temperature leaving. We inspected the filter and make sure all the components were working properly. Found defective zone board, we moved zone one to zone 5 to give the customer temporary heat until we installed a new one.