Fulton, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Fulton, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Fulton, MD
Goldberg - Fulton, MD
I was so impressed with my technician. He was thorough, knowledgeable and extremely helpful. Very professional. I am very pleased with everything but especially my technician.
On arrival set both units to call for cooling. Measure return temperature, supply temperature, amps, and voltage. Inspected electrical connections, replaced filters provided by customer, cleaned condensate drain line, and condensate drain pan, blower wheels are clean evaporator coils are clean. I found defective blower motor voltage absorption system for unit #2. I replaced it and tested it. Units are operating normal at this time.
I brought with me a 2 inch coupling and a small piece of 2 inch pipe. I cut the exhaust pipe where it screws into the furnace because 2 of 4 bolts were rusted out. I removed piping from inside the furnace and cut pipe above the furnace where I joined the new piping. Installed new Goodman exhaust pipe. Made all connections with primer and glue and made sure all drain line connections were back in place and secure. Cleaned up the area. Job complete.
On arrival inspected entire systems on heat and cool.found units in bad shape.found both indoor units motor leaking oil,which is a sign of failure .also both voltage absorption systems are weak .basement coil is rusted .in addition to ,the second floor outdoor unit is low on refrigerant (r22) and the hard start kit is leaking oil as well .units are 13 years old better to replace systems instead of repairs .
Service call on 01/16/18 On arrival set unit to call for heat unit is not operating normal fun motor running but no heat checked electrical connections checked drain checked flu pipe found the pressure switch stack open gave quote for customer accepted replacing the pressure switch tested checked electrical connections checked voltage and amps unit operating normal at this time. Collected $532 C.C
GOODMAN gas furnace service call Fulton Md
Completed heating maintenance on systems. Costumer installed nest thermostats and he wired them wrong . Wiring the 2nd floor system for a conventional system when it is a heat pump . Charged diagnostic time to switch the wires around .