Gambrills, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Gambrills, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Gambrills, MD
Very professional approach to service.
Stephan - Gambrills, MD
Yonis was very professional about the service. He took the time to explain everything to me and to answer my questions without appearing to need to get away fast to another appointment. I appreciated that. And, my compliments on what I think it is a good safety feature to send a message about the technician's arrival that includes a picture of the technician.
Spring Pm On 08/14/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter cleaned checked blower motor checked EWP and LWP also Temp checked all other electrical connections in side the unit unit operating normal at this time recommended UV lights installation and EZ trap to avoid future problems.
Upon arrival found indoor unit running but putting out 80 degree air. Refrigerant flowing through line set but liquid line very hot to the touch. Inspected outdoor unit and found condenser fan motor not running and compressor short cylcing on high pressure. Disconnected power and checked run capacitor, found capacitor at rating for compressor but failed for fan motor. Tried replacing capacitor and fan motor running normal now. Normal amp draws on fan motor and compressor. Indoor unit now operating with 18 degree split on air temps, 80 return air and 62 supply air. System cooling properly. Property management authorized work to be preformed with total of $350.
Denny inspected unit before tree falling, system working fine, customer states that tree falling from tree removal accident caused unit to stop working, Yonas inspected unit not working and suggested replacing condenser motor, fan, and capacitor. After replacing parts system now operating back to normal.
Service call on 05/28/19 On arrival set unit to call for cooling outdoor unit the compressor is coming but the fans is not running I checked electrical connections checked voltage and amps checked compressor capacitor capacitor it was low riding I gave quote for customer accepted start up still the fan motor is not running I was asking the customer how long he run the motor with out running he is telling me for 4days the motor and the fan blade has to be replaced I gave another quote for customer accepted order the parts we have to come back to finish the job.i Collected $702.50 deposit on CC
On arrival checked thermostat was calling for cooling. Measured EWT,LWT,EWP,LWP, delta P,delta T, measured return temperature, supply temperature, amps,and voltage. Inspected electrical connections, filter is clean,evaporator coil is clean, contactor, and voltage absorption system.when inspecting the blower motor I found the insulation on the left side of the blower was coming off, I used tape to put it back together. Explain to the customer the benefits of installing a uv light. Unit is operating normal at this time.
Fall pm on 01/11/19 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter is cleaned unit operating normal at this time.
When arrival we found unit not operating due to a defective high pressure switch, we replaced defective high pressure switch. We also checked refrigerant pressure. We left the customer house after the system was running correctly.
On arrival removed defective motor ,i then installed new Motor,tested it motor is operating normal ,i then check system operation and found pressure switch stuck open .system needs high pressure switch.system would only use electrical heat to heat at this time .
On arrival found unit not operating and locked on high pressure 68 times .found bad fan motor .customer refused to pay and would like to speak to alex .