Glen Burnie, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Glen Burnie, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Glen Burnie, MD
William - Glen Burnie, MD
Response from Supreme Air:
Thank you for taking the time to provide us this feedback. We think it's awesome that you had such awesome service. Have a supreme day!
on arrival found system low on refrigerant,added 1 lbs of 410 a refrigerant along with leak sealant.also checked caps ,coils ,contactor .customer signed up for service plan .unit operating normal at this time.
Replace the pressure switch. The inducer was pulling .93 iwc. Watch was rated for .65 but would not close. I tested the switch multiple times to confirm that the switch was faulty. I replaced the switch and cycled the unit multiple times. Unit operating normal. Customer signed up for service membership.
Fall pm on 12/05/18 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced found outdoor unit is not running checked electrical connections checked voltage and amps checked 24v found bud defrost board I gave quote for the customer he was tell me he have home warranty he is going to call them if replaced for him if is not he is going to call as back. also recommended to install humidifier and uv lights pm is completed.