Glenelg, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Glenelg, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Glenelg, MD
Fall pm on 12/20/18 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced units operating normal at this time.
Performed pm on 2 geo systems. Replaced provided filters. Flushed out drains with brush and hot water. Tested condensate pump. Inspected blowers and coils cleanliness. Measured specs of capacitors and inspected contactors. Tightened all electrical connections. Ran aux heat. Measured amp draw and heat rise. Ran geos. Measured amperage of compressors, blowers, and loop pumps. Checked delta loop pressures and temps as well as delta air temp across Evap coils. Units are operating normal. Customer has steam humidifier in crawl space for vertical geo. Found humidifier shut off at Humidistat and all drain piping disconnected from humidifier. Inspected further and found all pvc piping to humidifier needs to be replaced and corrected. Could not test humidifier because of repairs needed.