Hampstead, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Hampstead, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Hampstead, MD
On arrival set thermostat to call for cooling. Measured return temperature, supply temperature, amps, and voltage. Measured EWT,LWT,EWP, and LWP. I found water loop low on water pressure. Pressurized system to 70psi. Inspected electrical connections, contactor, replaced filter provided by customer, blower wheel is clea, evaporator coil is clean, cleaned condensate pan as well as the condensate drain line, and tested condensate pump. I noticed a lot of dust on the filter so I created and stimate for a duct cleaning. I also created an stimate for a wet switch. Customer was on a phone meeting so I couldnâ€™t explained the benefits of installing a wet switch and duct cleaning. But I will email him the information. Unit is operating normal at this time.
Called customer to tell him I would be there in around an hour customer would wife would like to pick diverter out anyway customer will call in when diverter are on site to get just labor estimate and installation
On arrival checked thermostat was calling for cooling. Measure EWT, LWT, EWP, LWP, delta P, delta T, return, and supply air Temperature. Measure amps,voltage, inspected contactor,voltage absorption system rated for 40, actual 40.1, filter is clean(28x30x2), blower wheel is clean as well as the evaporator coil. Checked operation and system is running correctly.
Performed maintenece on both rooftop units. Cleaned flame sensors. Ohmed igniters. Inspected heat exchangers, blowers, and coils. Checked capacitors and contactors. Tightened electrical connections. Replaced filters and belts. Ran heat and checked operation. Measured heat rise and amp draw. Let systems satisfy thermostat. Both units operating normal at this time.