Middle River, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Middle River, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Middle River, MD
Found unit without power . We found the breaker and turned it on . Unit has power of 118 volts . Checked operations and system is operating ,
Replace Inducer Motor and Assembly, belt and filters on carrier unit. Customer gave me gate code 3562 and door code 0232 and said he would meet me there. Upon arrival I went to roof and shut off power. Removed inducer Assembly and Wiring. Sanded down metal with old seal for clean surface. Installed new inducer Assembly with seal. Secured to panel and wired to unit. Replaced 4mfd run capacitor. Returned power to unit and jumped out heat. Removed jumper and replaced filters and belts. Ran Heat from thermostat and checked operation. No other problems found. Unit operating normal at this time. Customer not on site, did not sign.
Replaced water heater suspended in the ceiling , 6 gallon electric W/H
Upon arrival I went to RTU and could hear incuder running, no flame, blower not running. Opened up panels to find system faulted on inducer fault yet inducer is running. Shut off power and checked specs. Found capacitor out of spec. Put new one on to test but when starting unit I noticed inducer started right away but was running strange. Checked voltage and only had 200volts, needs 480v. Then thermostat called for heat and inducer started running at full capacity. Removed call for heat and inducer kept running but was making some noise and started to smoke. Ohmed out motor terminals and found we have a short in the inducer motor, making it run 24/7 and at lower voltages. When only supplied 1 leg of power, the inducer tries to run and is shorting out. Verified tha board is sending out correct voltage and operating normally. Need to replace inducer Assembly. Also found belt is very worn and filters are very dirty. Also checked heat exchanger, didnâ€™t find any cracks but can see a decen
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked filter,coil,safeties ,cap was low and blower was dirty .unit is operating normal at this time
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked coil,cap ,heat exchanger.found blower dirty and cap below manufacturer specs.unit operating normal at this time .
Took off $25.50 because I messed supply line and is lookin for some new ones to install. Have to come back to install new supply line..