Middle River, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Middle River, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Middle River, MD
Upon arrival I spoke with manager inside who called building management company and got the roof ladder code. Went to roof and uploaded equipment info. Gave office filter and belt sizes. Went to supply house and picked up filters and belts. Returned to replace filters and belts. Inspected coils and blowers. Checked capacitors and contactors. Tightened electrical connections. Ran heat and checked operation. Measured heat rise and amp draw on both units. Let systems satisfy thermostats. Both units operating normal at this time.
Upon arrival I was told that thermostat was fluctuating in temp and customer wasnâ€™t sure if Geo was working properly, when switched to emergency heat system satisfied relatively quickly. During diagnostics I found Geo running at first stage but fan speed running at max capacity, which was lowering output and made system run too long, making loop cold. Rewired board for LoY and Y2 so fan runs at proper speed for both stages. Then I found adaptive recovery on for thermostat, turned off. Finally I increased compressor lockout from 15 degrees to 30 degrees. Informed customer to keep emergency heat on for today because loop is cold and is affecting performance. Turn Geo back on tomorrow, loop needs to warm up. Unit operating normal at this time.
The White Rodgers thermostat was dropping voltage when it tried to run 2nd stage compressor heat mode. I showed the customer what was going on so they could understand the problem. I charged the unit to specification in first stage because it never would go into 2nd stage last week. The old thermostat had no test mode either. I did not suspect any refrigerant problems when I put my gauges on. I checked heat of extraction was at 40,000 btu which was above printed material of 35,700. Temperature rise more than 30 degrees. I took a picture of the measurements. I installed lyric thermostat. I ran into a problem because the outdoor temperature sensor was three wire. I had to replace with Honeywell 2 wire. Unit operating normal.
Service call on 01/21/19 On arrival the condensation pump keep running also the pan full of water the problem was the condensation tube frozen up no water going out I run the tube to the washing drain line in side the house checked electrical connections tested unit operating normal at this time. Everything under warranty no charge.
There is evidently a pin hole in the evaporator coil. I saw traces of oil on the pan under the coil. I mentioned coil replacement as an option but customer and I agreed that using internal leak sealer and recharging is a better option. I added the leak sealer and charged the system until it matched printed specification data and had normal operating pressures and temperature rise and heat of extraction as well. Unit operating normal.
Found unit without power . We found the breaker and turned it on . Unit has power of 118 volts . Checked operations and system is operating ,
Replace Inducer Motor and Assembly, belt and filters on carrier unit. Customer gave me gate code 3562 and door code 0232 and said he would meet me there. Upon arrival I went to roof and shut off power. Removed inducer Assembly and Wiring. Sanded down metal with old seal for clean surface. Installed new inducer Assembly with seal. Secured to panel and wired to unit. Replaced 4mfd run capacitor. Returned power to unit and jumped out heat. Removed jumper and replaced filters and belts. Ran Heat from thermostat and checked operation. No other problems found. Unit operating normal at this time. Customer not on site, did not sign.
Replaced water heater suspended in the ceiling , 6 gallon electric W/H
Upon arrival I went to RTU and could hear incuder running, no flame, blower not running. Opened up panels to find system faulted on inducer fault yet inducer is running. Shut off power and checked specs. Found capacitor out of spec. Put new one on to test but when starting unit I noticed inducer started right away but was running strange. Checked voltage and only had 200volts, needs 480v. Then thermostat called for heat and inducer started running at full capacity. Removed call for heat and inducer kept running but was making some noise and started to smoke. Ohmed out motor terminals and found we have a short in the inducer motor, making it run 24/7 and at lower voltages. When only supplied 1 leg of power, the inducer tries to run and is shorting out. Verified tha board is sending out correct voltage and operating normally. Need to replace inducer Assembly. Also found belt is very worn and filters are very dirty. Also checked heat exchanger, didnâ€™t find any cracks but can see a decen
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked filter,coil,safeties ,cap was low and blower was dirty .unit is operating normal at this time
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked coil,cap ,heat exchanger.found blower dirty and cap below manufacturer specs.unit operating normal at this time .
Took off $25.50 because I messed supply line and is lookin for some new ones to install. Have to come back to install new supply line..