Millersville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Millersville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Millersville, MD
Goddard - Millersville, MD
They were quick in coming out and the service was great. The gentleman was very efficient and took the time to explain everything.
To replace sump pump with proflo .3 hp sump pump.... Replaced .3 hp sump pump with new proflo .3hp sump pump filled basin multiple times pump works properly
Case #439629 . Spoke with Dave from waterfurnace and we confirmed that the master stat isnâ€™t sending the call for humidity. Recommend replacing . Checked operations on humidifier and it is operating properly .
Upon arrival I was told that 2nd classroom on left side of building first floor was blowing cold air and doesnâ€™t have heat. Also, 2nd floor classroom on the left would intermittently blow cold air but system is satisfying. Found first floor classroom RTU wasnâ€™t getting gas. Found maxitrol pressure regulator stuck or frozen. Tapped it a few times and gas released. Had manometer on system and checked pressure. Operating normal now but quoting to replace Maxitrol regulator. Then inspected 2nd floor system. Found unit operating normal but thermostat settings making unit blow cold air. Disabled fan with heat option, unit does this already and fan is being cycled too quickly during call for heat, blowing cold air at first. Then I found unit was programmed for adaptive recovery, causing unit to cycle on before schedule asks it to. Removed adaptation recovery. Tested unit and found it is operating normal.
I ran hot water with a prop shut off valve to the new humidifier. Replaced drain line with pvc. Tested unit for operation and for any water leaks. Humidifier is operating normal. Disregard remaining balance. Customer is paid in full.