Monkton, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Monkton, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Monkton, MD
Spring Pm On 08/07/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked air filter and replaced checked EWP and LWP also Temp checked compressor capacitor checked all other electrical connections in side the unit tested units operating normal at this time highly recommended duct cleaning and Uv lights installation.
I pressurized the ground loop to 65 psi and confirmed proper flow rate and heat of rejection. The drain was very slow to drain, but cleaning the drain pan and drain line is part of the maintenance. I poured water through the drain after cleaning and it drains quickly. I checked the electrical wiring and electrical systems, all are within specification. Unit cooling with 20+ degree across the evaporator coil. Unit operating normal. Iâ€™m regards to customer concern with stale odors from the unit and previously been told about ultra violet lights, I informed the customer that W.F. prohibits UV lights from shining on the coil surface, either front or back. I suggested Apco Air Scrubber as a better solution. I sent product literature to the customer and made an estimate.
Spring Pm On 04/23/19 On arrival set units to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced checked EWP and LWP also Temp it was low I pump back up to 55/50 psi checked all units compressor capacitor for unit #2 the voltage absorption system was well below spec so I suggested replacing now to avoid future problems I gave quote for customer accepted replaced the capacitor I tested start up and unit began operating very smoothly with out any hesitating or lag all units tested units operating normal at this time. Highly recommended to installation UV lights and whole house surge protection. Collected $135.00 for capacitor replacement On check #1362
Removed old blower motor . Cleaned blower wheel and housing . Installed new motor with new capacitor and checked operations . Costumer needs to replace 20x20x1 filter because it is plugged solid with dirt . Left thermostat off unit filter is changed . System is operating
On arrival found bad indoor motor and weak voltage absorption system also found dirty blower wheel .need to replace motor and absorption system and clean blower wheel .unit is not operating normal at this time. Mr hicks paid half .
Fall pm on 01/03/18 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced also found lot of dust in side the unit highly recommended to install UV lights unit operating normal at this time.
GEO WATER FURNACE FALL PM MONKTON MD