Mount Airy, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Mount Airy, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Mount Airy, MD
Called customer and he informed me that nobody would be home during service. During diagnostics I found no LED lights at boiler or zone panel. Checked voltage and found none at boiler. Got access to basement of house per customer and I found 20amp breaker tripped. Reset and tested unit operation. Also labeled breaker. Found 10amps total ONLY when boiler is firing up. During normal operation I found unit was pulling 6.5amps total. Checked operation of pumps, boiler, stat, and zone control. Amp draw readings taken were from main power at breaker reading all motor amperages. Found P/T sight glass on boiler is full with water and difficult to read. Continued to run system and found no additional problems. Suggest 20amp breaker get replaced, possibly weak and prematurely tripping. Left system running to make sure Desert Aire System satisfies and customer sees that it is working. Locked basement door and front pool door. Left back pool door unlocked. Office please follow up with customer. N