Nottingham, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Nottingham, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Nottingham, MD
Lance - Nottingham, MD
I foolishly thought our thermostat was faulty; Chris' experience led him to look deeper into the situation and realize that a fuse in the furnace needed replacing. Within 20 minutes, the system was up and running. Great job
Coil sensor is faulty and not closing. Heat pump froze up severely several times. I did force defrost and after that the refrigerant pressures were normal and temperature rise was 24-26 degrees. I think itâ€™s best to replace the defrost board and sensors together and called the service manager. I completed a parts order form.
I replaced the heater pack and installed the breakers it came with. I checked the unit for proper operation. Unit operating normal. Customer owes no more for this repair once the previous payment of $440 is applied to the balance. I told customer I will come back on April 9th at 3pm as a courtesy to check the unit in ac mode. I will let the office know to set time for this.
Heater kit needs to be replaced. There is a short somewhere within the 60 amp side. I removed the wires to the 2 elements served by the 60 amp side so that the board still has power but the fuses will not be able to blow. It is of course only heating on heat pump heating and 5 kw of auxiliary heat. Customer approved the repair to replace the heater kit and per Alex, I credited back the amount paid previously. I filled out a parts order form and sent it to the person in the office to order tomorrow. Please reach out to the customer with availability.
Replace blown 60 amp fuse and test the system. I replaced the blown 60 amp bullet fuse and tested the unit. Refrigerant pressures were normal for very low outdoor temperature. Auxiliary heat came on and was pulling normal amps. The unit is operating normal. Customer declined service membership due to them moving from the home soon.
1/3 hp disposal leaking from bottom remove old disposal and replace with new 1/3 hp disposal
I replaced the filters for each unit and the blower belt for unit #1. I operated the units in first stage and auxiliary heat stages. Units have normal temperature rise in first stage and auxiliary heater strips are working properly on each unit. I checked the electrical wiring and electrical systems. The units are operating normal. Unit #1 and #2 are very old and I strongly recommend replacing these units. Unit #2, the smaller tonnage Carrier roof top unit has a faulty disconnect on the roof. I turned the power off to service the system and when I was ready to leave the roof, I noticed it never started working. I removed panels again and had no voltage. I opened the disconnect and had power coming in. I pulled the fuses and they were in tact. I finally concluded that the disconnects teeth do not make good contact with the main voltage when it is turned on. I managed to maneuver the handle and the voltage returned. Ultimately it is not reliable and unsafe for any technician that goes
Replace o ring on single handle shower diverter cartridge