Odenton, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Odenton, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Odenton, MD
Brian - Odenton, MD
On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced checked condenser unit checked pressure checked refrigerant i found low refrigerant 48 psi and R22 riding 27 not obviously like also the run capacitor is low riding I gave quote for customer customer accepted just to charge the refrigerant customer he have planned to replace the hole unit I charge 1.13 pounds of refrigerant R22 unit tested unit operating normal at this time. Recommended to replace the run capacitor for condenser unit also duct needs to be cleaned. Collected $515 for add refrigerant R22 1.13 pound also $59 for tune Up total $574 on C.C
Completed AC maintenance
To replace 40 gallon gas water heater with atmospheric vent , will need to bring heater through house no basement door access , will need to install expansion tank and pan as well
Upon arrival I was told that furnace was working but inspector asked them to have furnace looked at to address a few items. Went to furnace and ran heat. Inspector mentioned a yellow flame but I do not see that. Flame is blue with small trails of orange deep inside of heat exchanger which is normal. I did find gas pressure slightly high, 3.75inches, lowered to spec at 3.5inches. Also found a good amount of air bleeding from small gaps in unit. Used tape to seal air gaps. Continued to run furnace and found heat rise of 43, normal. Filter is clean, blower and coil are clean. Unit is pretty new and is operating normal at this time.
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked coils,blower ,cap,contractor .unit operating normal
Upon arrival I found furnace off. Turned on to find inducer motor not running, only humming. Capacitor in spec and motor getting correct voltage. Quoted customer to replace inducer Assembly and he approved and paid half. Office please contact customer with update on part and to schedule return. 12-7-18 (DM) replaced inducer motor assembly and checked operations . Adjusted fan speed to get unit into specs. System is operating but poorly. The system makes a lot of noise from blower motor but everything is tight and in-line with amps . Unit is 23 years old so I informed the costumer about the noise and the life expectancy of the furnace . Supply air 131 degrees and return air 80 degrees .
Upon arrival I found furnace off. Turned on to find inducer motor not running, only humming. Capacitor in spec and motor getting correct voltage. Quoted customer to replace inducer Assembly and he approved and paid half. Office please contact customer with update on part and to schedule return.
Called customer at 740, no answer, left vm. Called again at 750 and no answer. Waited another 15 mins and no call back.