Owings Mills, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Owings Mills, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Owings Mills, MD
Good response time
Lorraine - Owings Mills, MD
Collin was professional and knowledgeable
Review of today's appointment
Curtis - Owings Mills, MD
Genevieve - Owings Mills, MD
Yearly preventative maintenance
Holt - Owings Mills, MD
Exactly What We Needed, At the Right Price
Anton - Owings Mills, MD
Professional. On-Point. No BS or high pressure to rack up the amount of the bill.
On arrival checked thermostat was calling for cooling. Measured return temperature, supply temperature, amps, voltage, voltage absorption system. Inspected electrical connections, customer has the wrong filter size, used a vacuum to clean condensate drain line, and contactor is ok. Customer is due for service agreement renewal, but she was in a meeting so she will renew it with the office.
There was a small spot of water still left in basement between water heater and furnace and water spot was larger but most had dried up. I checked every fixture and drain including sump pump ran and emptied washer both toilets kitchen and both bath sinks and upstairs tub could not recreate water in basement or visibly see Any leak. Advised resident to take picture of water if it happens again and above and below to try and find possible issue. Leak is not coming from new water heater installed pan is dry and no signs of water being in it all press joints are dry and not leaking. Water heater is not leaking. If issue happens again will have to charge for diagnosing issue because it is not a warranty on the water heater we installed. Did find clean out cap on sewer line in basement not screwed in very tight I did tighten clean out plug just in case water was coming out after a lot of water coming down at once
Customer was smelling gas after water heater was installed. Checked all connections on gas line and control valve found gas leaking from thermo coupling where it screws into gas control valve screw was cross threaded loosened screw and removed tube straightened out supply tube and retightened nut turned on gas and tested leak stopped found no other issues on any gas connections. No charge to customer warranty call
Removed defective gas valve replaced with new
Replace 40gallon gas water heater. Claimed Angieâ€™s list deal for $1149.00 for a 40 gallon gas water heater Found fitting that needed to be replaced above the old valve gave $325 estimate customer approved over the phone To cut nd replace 3/4â€ cpvc transition fitting and tee Replaced 40gallon gas water heater with new AO Smith , removed od tank ,installed pan and expansion tank. Cpvc tee above valve for existing expansion tank was leaking cut out and replaced , installed expansion tank in new location on copper line instead of cpvc for stability, installed full port ball valve with bleed as well After reconnecting the gas line , attempted to light heater , was unable to get heater lit , check gas valve and valve at meter , no issue with gas , spark igniter push button is not clicking or activating the spark igniter , called into AO smith customer service was not called back at this time will need to get new gas valve through warranty and come out to swap out when itâ€™s availa
Will return Monday to replace 40 gallon gas water heater.
During operations inspection I noted that unit #2 & #3 had pitted and burnt blower motor contactors. I finished the operations inspection and went back on the roof to replace the parts. I tested each unit to ensurse proper operation after replacing the parts. Both units are operating normal.
I replaced the filters for each unit. I tensioned the blower belts again since they had worn slightly since being replaced. I cycled the units through all modes of operation. Unit #2 & #3 need to have 2) 2pole contactors for the blower motors replaced. Otherwise all units are operating normal.
Replace omen single handle positemp cartridge in master bath shower.
3 compartment sink near dishwasher was leaking from neck of faucet spout removed faucet neck and replaced both o rings inside reinstalled tested not leaking. Electrical cord on wing sauce station was broken cut broken section out and used but connectors to reattach wrapped cord with electrical tape to cover up connections. Bottom drawer on grill would not close screw broke and caused tracks for drawer to mot be aligned drilled out broken screw and used self tapping screws to re secure track drawer opens and closes properly now. Sheet metal lining on left side of double door freezer came out of gasket was able to remove sheet metal and flatten to remove bend Re installed sheet metal and gasket secured in place with self tapping screw door closes now but would recommend having gasket replaced on both doors as neither of them seal firmly
Will order cartridge and return to install at later date
Replace the heating control board with new sparkler assembly. Upon arrival I went to system and tested operation. Verified control board not sending voltage to Igniter, found slight burn mark behind board. Removed old furnace control board and replaced with new. Swapped wire to wire and checked connections. Returned power to system and tested heat. Spark Igniter lit flame and unit started heating. Continued to test and checked heat rise and amp draw. Unit operating normal at this time.
Fall pm 02/12/19 on arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter is cleaned unit operating normal at this time.
Angieâ€™s list service call
Chris was here on the 9th and found bad control board and spark igniter . We need to come back and replace parts to get unit up and running. Space is at 70 degrees now .
Upon arrival customer informed me that furnace stopped working last night. Was suspecting Thermostat because she took it off the schedule and into a hold, system started working afterwards. During diagnostics I ran heat and checked operation. Found slightly high heat rise. Shut off unit and recalled last fault, high limit fault. Checked airflow and found it was moving enough air. Replaced provided filter to verify no restrictions. Put manometer on gas valve and ran heat. Found low stage heat at 2.2inches w.c. Lowered to spec at 2.0inches. Found high stage heat at 3.9inches w.c. Lowered to spec at 3.5inches. Heat rise now normal. Found no additional problems. Unit operating normal at this time. Filter size for customer is 16x22x1
Warrantied per Alex. Upon arrival customer informed me that new furnace stopped working yesterday but is working today. During diagnostics I found condensate line clogged up to furnace, tripping pressure switch. Traced pvc and found it exits outside near condenser and is frozen solid. Found emergency pan and main drain line were flipped during install. Old pvc pipe was running underneath furnace drain which was causing it to freeze back into pipe. Swapped drain lines and tested operation. Unit operating normal at this time.
Call was sent to the sales department. Customer would like estimate on ductwork.
I replaced the filters and belts for each unit. I made sure that the belts were properly tensioned. I then checked the operation of the units in heating mode. Units #2 and #3 are operating normal. Unit #1 goes into a lockout because the spark igniter never gets voltage from the control board. The inducer works, the pressure switch closes, all safety devices are closed and the gas valve opens but never ignites. I made an estimate to fix this unit and also got part numbers for the parts needed. This unit is not operating at this time and will not heat until the board and spark igniter are replaced.
On arrival found outside unit breaker tripped ,found bad outdoor compressor .unit is not operating normal.customer bought new system
Fall pm on 12/31/18 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced also found EWP and LWP is low pump it up to 60psi customer needs to cleaned the humidifier I gave quote for customer accepted cleaned checked electrical connections checked voltage and amps checked drain and clean also replaced the humidifier pan unit operating normal at this time. collected $156 CC
Fall pm on 12/14/18 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced recommended install uv light unit operating normal at this time.