Parkville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Parkville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Parkville, MD
UV Light install and service
Bath - Parkville, MD
Youssef is very friendly and personable as well as a fine technician.
Response from Supreme Air:
Mr. Bath thank you very much for the great review! Supreme Air is lucky to have such a fine technician on our team! Have a Supreme day!
AC unit repair.
Lou - Parkville, MD
Good prompt professional service. Expensive.
Installed 50 gallon gas water heater in basement , tested no leaks no issues
On arrival we checked thermostat was calling for heat, then we went to the basement and found water heater was leaking. We also found dirty duct. System is operating normal, but it is in a bad shape. Customer is schedule for a free inspection in may. Customer full payment to replace the water heater today.
Auger basement toilet cleared blockage
On arrival found system not operating,found system with bad circuit board also heat exchanger is cracked ,unit is in bad shape best to replace
Completed heating maintenance. Costumer has black marks on his screen which makes it hard to read the screen . Gave costumer a quote to replace thermostat .
Cut out old 3â€ pvc vent pipe and install new pipe inside wall
Service call 12/15/18 On arrival set units to call for heat the blower is running but no heat checked electrical connections checked voltage and amps found out is roll out switch trip reset the switch turned on the unit when the burner started the switch is tripped again gave me flashing codes checked the chimney checked the air filter everything is okay my recommendation to replace the heat exchanger customer is going to call us Monday what he decided I shut off the unit and I put tag. Collect $290 diagnostic fee and $129 trip fee total$419 on check #1773
Upon arrival I spoke with GM and informed him of what I was doing. Went to regulator and opened valve. Leak tested all piping and found no leaks. Went to both units and opened up hand valve then leak tested again, found no leaks. Returned power to units and tested incoming and outgoing gas pressure at gas valves. Used jumper to do so at the roof. Rear unit 2nd stage gas pressure was a little high, 3.7inches w.c, lowered to 3.5inches. First stage was correct gas pressure. Front unit had correct gas pressure as well. Shut down units and removed jumpers. Spoke with GM and he turned the units on from thermostats. Went back to roof and checked operation. Normal heat rise and amp draw. Units both satisfied and are operating normal.
On arrival installed new apco air purifier.tested it ,unit operating normal
On arrival found unit not operating,found system locked on limit found very dirty filter also thermostat loosing display.also duct very dirty .unit operating normal but thermostat may break .
On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked coils,caps,Contactors,replaced filter,found voltage absorption systems all under manufacturer specifications.also indoor coil for basement unit is dirty .units are operating normal at this time
Sewer injector pit has locked up due to years of debris and debris from wash machine. Recommend sewer injector pit be cleaned and install new sewer pump. Nov. 21, 2018 new injector pit install, tested , pit clean, and surrounding area.