Parkville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Parkville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Parkville, MD
UV Light install and service
Bath - Parkville, MD
Youssef is very friendly and personable as well as a fine technician.
Response from Supreme Air:
Mr. Bath thank you very much for the great review! Supreme Air is lucky to have such a fine technician on our team! Have a Supreme day!
AC unit repair.
Lou - Parkville, MD
Good prompt professional service. Expensive.
Upon arrival I spoke with GM and informed him of what I was doing. Went to regulator and opened valve. Leak tested all piping and found no leaks. Went to both units and opened up hand valve then leak tested again, found no leaks. Returned power to units and tested incoming and outgoing gas pressure at gas valves. Used jumper to do so at the roof. Rear unit 2nd stage gas pressure was a little high, 3.7inches w.c, lowered to 3.5inches. First stage was correct gas pressure. Front unit had correct gas pressure as well. Shut down units and removed jumpers. Spoke with GM and he turned the units on from thermostats. Went back to roof and checked operation. Normal heat rise and amp draw. Units both satisfied and are operating normal.
On arrival installed new apco air purifier.tested it ,unit operating normal
On arrival found unit not operating,found system locked on limit found very dirty filter also thermostat loosing display.also duct very dirty .unit operating normal but thermostat may break .
On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked coils,caps,Contactors,replaced filter,found voltage absorption systems all under manufacturer specifications.also indoor coil for basement unit is dirty .units are operating normal at this time
Sewer injector pit has locked up due to years of debris and debris from wash machine. Recommend sewer injector pit be cleaned and install new sewer pump. Nov. 21, 2018 new injector pit install, tested , pit clean, and surrounding area.