Perry Hall, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Perry Hall, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Perry Hall, MD
Service call on 06/02/19 On arrival set unit to call for cooling indoor unit operating normal I checked electrical connections checked voltage and amps checked filter checked condenser drain checked all other electrical connections I go outdoor unit is not running all electrical wires is burnt I explained the customer what happened I showed the customer I suggested replacing to operating outdoor unit also I suggested to add hard start kit to avoid future problems I gave him a quote customer accepted I replaced the capacitor replaced the contactor also add hard start kit and rewire all electrical connections I tested start up and unit began operating very smoothly without any hesitating or lag checked electrical connections checked voltage and amps measured supply and return air I checked the pressure and theyâ€™re ideal indicating zero leaks compressor running fine unit operating normal at this time. Collected $1248.55 on CC
On arrival set units to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections inspected drain ,coils,caps,blower motors ,units are operating normal at this time
Upon arrival I found thermostat in off position, customer explained unit was running in ac mode no matter what they asked Thermostat to do. Found thermostat not wired or programmed properly. Customer has boiler as heating unit, attic system is ac only. Had to rewire thermostat for correct operation. Also found jumper for RH and RC still connected, removed because systems are seperate. Changed configuration to hot water heat and conventional ac. Returned power to both boiler and AHU and tested operation. Both heat and ac operating normal. Customer asked me to leave mode off. Since I removed RH and RC jumper, and customer thinks the threw away box, I taped jumper to AHU in attic Iâ€™m case it needs to be used in the future.
Tune Up on 04/10/19 On arrival customer explained to me he has problems with thermostat he changed the battery than the thermostat is not operating I checked the thermostat is not operating normal customer has his On thermostat I gave quote he accepted install new thermostat tested checked electrical connections checked voltage and amps inspected measured supply and return air temp checked condenser unit outdoor checked electrical connections checked voltage and amps checked coil highly recommended outdoor door unit needs run capacitor also contractor and coil needs to be cleaned. I explained the customer to replace the unit he needs talk to someone about the price from the office also customer sign New service agreement. Collected $201 for thermostat installation also $16.66 for New service agreement total 217.66 on check #978 for monthly payment customer needs some one call from the office. Unit tested unit operating normal at this time.
Install 2 sump jet system in basement sumpumps tie into existing drain and water lines
Customer paid half deposit of 627 and another 627 due upon completion
02/01/19 On arrival replaced the capacitor tested checked electrical connections checked voltage and amps measured supply and return air temp unit operating normal at this time. Collected $323.85 On C.C
Fall pm on 01/28/19 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced recommended to replace run capacitor I gave quote for customer customer accepted I donâ€™t have one in truck I ordered we have to come back to replace the capacitor unit operating normal at this time.No payment collected customer pay full of the balance when we finish the job. $323.85
Fall pm on 01/17/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced unit operating normal at this time.