Severn, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Severn, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Severn, MD
Upon my arrival the unit was running in cooling mode. I had 75 return and 60 supply, which is only 15 td. I went to the outdoor unit and applied my refrigerant gauges and had low suction and low discharge pressure with both high superheat and subcooling. I isolated the sensing bulb and in the process of doing that noticed a large puddle of water in the bottom of the duct under the coil. Heating and cooling the bulb resulted in little to no change of suction pressure and as the unit runs the subcooling gets higher and higher. The unit need to have the txv valve replaced. Customer approved this repair and paid $600. I completed a parts order form for the parts needed. I told the customer the office will call to schedule return visit to fix the system. The unit is operating some so customer does have some cooling in the meantime.
On arrival found system not working correctly,found system had leaked out all the refrigerant.i then presssurized system with nitrogen ,I couldn't find any leak .pressure held at 350 ,also vacuumed system and held at 500 microns .i recharged system with 67oz of 410 ,tested it ,unit operating normal
Diagnosis of tapping sound not plumbing related.
Spring Pm on 05/17/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced checked in water pressure and out water pressure also checked water temp checked all other electrical connections unit tested unit operating normal at this time.
On arrival set unit to call for cooling. Measured return temperature, supply temperature, amps, voltage, EWT,LWT,EWP,and LWP. Inspected electrical connections, filter is clean, evaporator coil is clean, blower wheel is clean, pressurized system to 60psi, cleaned condensate drain line and condensate drain pan. Unit is operating normal at this time.
Hot water heater flue pipe was not secured properly and fell off the tank. I mounted it securely and sealed up any cracks or screw holes with aluminum flue tape. I took before and after pictures for warranty reasons.
Spring Pm On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter cleaned checked condenser unit checked electrical connections checked voltage and amps checked coil checked compressor capacitor checked pressure tested unit operating normal at this time.
Installation of Amana Heat Pump Air Handler MN# ASPT37C14 S# 1901050544 Heat Pump MN# ASZ160361 S# 1812167176 Total Job $6454.00
To replace 50gallon gas water heater , will need ballvalve , and pan expansion tank is still good and looks new , heater is from 1996 Ac unit Coil is rusty and dripping and pan in unit is full of water Installed 50gallon gas water heater also installed ball valve and expansion tank as well
On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections inspected drain and cleaned it,inspected coils, blower,caps,contactor .unit operating normal
Upon arrival I spoke with customer and him and he didnâ€™t have a problem with furnace, only wanted to get system inspected. He and Donna spoke and it was agreed that for $99 I would inspect his furnace. Capacitor in spec, flame sensor a little dirty but correct spec, ignitor in spec. Inspected heat exchanger, good. Blower clean. Filter has decent amount of dust, customer may want to consider duct cleaning. Ran furnace and found normal heat rise and amp draw. System operating normal.
On arrival checked thermostat was calling for cooling. Measured EWP,LWP,EWT,LWT. measured return and supply temperature, amps, voltage, inspected electrical connections, blower wheel is clean, evaporator coil is clean, used a vacuum to clean condensate line, and replaced filter provided by customer Aprilaire 413. Customer is moving out. Unit is operating normal at this time.
Completed AC inspection .n
Upon arrival I found furnace firing up then flame shuts off due to low flame sense. Quoted customer to replace but he declined for now. He may be considering replacing soon, furnace and ac 14+ years old.
Fall pm on 02/11/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters unit operating normal at this time.
On arrival checked thermostat was calling for heat, inspected EWP,LWP,EWT,LWT, electrical connections, voltage, AMPS, and also replace filte(size413). Unit is operating normal.
Fall pm on 02/01/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced unit operating normal at this time.
Vent pipe not secure going thru roof secure vent pipe and reseal
Furnace is in the basement with the exhaust going out of the back of them home . Leak is on the first floor ceiling under the washer . Would need to cut ceiling open to find problem . Costumer needs to talk to property owner .
Fall pm on 12/06/18 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters recommended to install UV lights unit operating normal at this time.
The compressor voltage absorption system (run capacitor) was rated for 30 and had a value of 8.36. Therefore the compressor could not start or run. Customer had turned the heat off last night, otherwise the auxiliary heat would have kicked on. I made sure the auxiliary heat strips did operate. I replaced the part with a 30uf single run capacitor with a start value of 30.35. I cycled the unit to make sure it would operate and checked the temperature rise: 25.4 degrees in second stage heat mode, which is within comfort range and units specifications. Unit operating normal. I retained the depleted capacitor to return to Water Furnace. I also spoke with the customer about the Intellistart modules.
Service Agreement Renewal
Completed tune up . Gave costumer quote to check humidifier and also to level out her outdoor unit . Also there is a sensor fault coming up on thermostat . System is operating properly , would have to run service to figure out issue . Costumer paid in cash . Took a picture of it and will turn into Jackie .