Severn, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Severn, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Severn, MD
Fall pm on 02/11/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters unit operating normal at this time.
On arrival checked thermostat was calling for heat, inspected EWP,LWP,EWT,LWT, electrical connections, voltage, AMPS, and also replace filte(size413). Unit is operating normal.
Fall pm on 02/01/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced unit operating normal at this time.
Vent pipe not secure going thru roof secure vent pipe and reseal
Furnace is in the basement with the exhaust going out of the back of them home . Leak is on the first floor ceiling under the washer . Would need to cut ceiling open to find problem . Costumer needs to talk to property owner .
Fall pm on 12/06/18 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters recommended to install UV lights unit operating normal at this time.
The compressor voltage absorption system (run capacitor) was rated for 30 and had a value of 8.36. Therefore the compressor could not start or run. Customer had turned the heat off last night, otherwise the auxiliary heat would have kicked on. I made sure the auxiliary heat strips did operate. I replaced the part with a 30uf single run capacitor with a start value of 30.35. I cycled the unit to make sure it would operate and checked the temperature rise: 25.4 degrees in second stage heat mode, which is within comfort range and units specifications. Unit operating normal. I retained the depleted capacitor to return to Water Furnace. I also spoke with the customer about the Intellistart modules.
Service Agreement Renewal
Completed tune up . Gave costumer quote to check humidifier and also to level out her outdoor unit . Also there is a sensor fault coming up on thermostat . System is operating properly , would have to run service to figure out issue . Costumer paid in cash . Took a picture of it and will turn into Jackie .