Severna Park, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Severna Park, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Severna Park, MD
Long Time Customer
Matthew - Severna Park, MD
Sent over estimate for repairs on well pump and filter to Ben from Annapolis property management he will get with homeowner and let us know about approval
Unit is off on low pressure . System has no refrigerant in it and system is R22 . Recommend replacement , called office and let them know and scheduled for a time for sales to come out .
On arrival we checked thermostat was calling for heat, checked EWP, LWP,EWT,LWT, electrical connections, contactor, amps, voltage, replaced filter(size 413). Water pressure was low, we added water(50psi). Unit is working correctly.
Upon arrival I called Lauren because I found nobody on site. Customer gave me lockbox code so I went into store and found both thermostats reading 66 and calling for 75. Went to roof and found back unit operating normal and system putting out 100 degrees. Unit supplies classroom but thermostat is outside of room so thatâ€™s why it is still calling for heat. Room temp is about 80 so I left classroom door open to help even out space temperature in building. Then I went to front unit and found low temperatures. Found economizer door screws had become loose so the door had fallen, creating a return temp of 50 degrees because it was pulling in a lot of outdoor air. Put door back into place and continued to test. Found only 1 out of 3 legs working for aux heat. 1st leg wonâ€™t come on due to bad sequencer. 2nd leg wonâ€™t run because heater coil is bad. Quoting customer to replace entire heater pack because 1 coil is already broken and speculating the others will follow because of age and am
Called Lauren and had to leave a voicemail. Called studio and spoke with Chris. He informed me that they were suspecting a problem yesterday but today heat is working and they havenâ€™t seen a problem. He said he was going to contact Lauren as well to confirm if they need service.
To drain down boiler , remove baseboard and cover from wall , cut down pipe 28â€ re drill the hole for the pipe to go into the basement and reconnect in basement , customer will cut down baseboard wall plate and cover for baseboard to size. Will return Monday to complete work customer paid $233.00 , down will pay the rest at completion of the job.
Fall pm on 01/04/19 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and cleaned recommended duct cleaning and Uv lights also blower motor capacitor is low riding need to be replaced unit operating normal at this time.
Replace 50 gallon electric water heater also install new pan ball valve and expansion tank
Fall pm on 11/28/18 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced unit operating normal at this time.