Silver Spring, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Silver Spring, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Silver Spring, MD
Dave - Silver Spring, MD
Technician Yonas Mengesha was great, explained everything he did. Would recommend to anyone based on this experience.
Mr - Silver Spring, MD
On arrival Drained water down ,removed old canister ,i then installed new canister .tested it .unit on normal
On arrival found unit not operating normal due to a defective condensate pump. I replace it, tested it, and unit is operating normal at this time.
On arrival found thermostat blank ,found condensate pump not operating despite of existing power .found bad pump .need to replace the condensate pump ,customer paid in full
Fall pm on 03/11/19 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced checked water pressure in and out unit tested unit operating normal at this time.
Paid $58 trip charge in cash
On aarrival found arrival found bad pump .replaced it ,tested it .unit operating normal .also found steamer canister need to be replaced ,need to come back to replace it .custmer paid in full
I put my gauges on true suction and the discharge line in heating mode and cycled the unit. There was no difference of refrigerant pressures and the compressor turned off and on multiple times due to internal overload. I changed high pressure gauges to discharge line in cooling mode and cycled the unit in cooling mode and had the same thing happen. The compressor is not pumping the refrigerant. It has become internally damaged and must be replaced. I called the owner of the property and gave them the estimate and offered a service membership. Customer needs to contact home warranty company first before approving the repairs. I completed a part form (estimate) so that the correct compressor can be ordered once approval is given.
At the thermostat I found the auxiliary heat differential set to .5,.5,&4.0. The auxiliary heat never came on and the compressor was running constantly never giving the water in the loop time to recoup heat. I reset to factory default setting of .5,.5,&.5. I checked to make sure auxiliary heat strips were working properly. I checked the capacitor and it is within specification. I ran unit on second stage heating mode. I reduced the pressure drop to 4 psi from 7 psi and checked heat of extraction. All normal. Temperature rise 30 degrees. Unit is operating normal. I recommend adding an Intellistart Module the compressor circuit. Customer skeptical of the benefits so they will read more about the benefits even though I tried my best to explain them. I made an estimate for this repair.
To install customer supplied kitchen faucet and swap soap dispenser... installed customer supplied moen kitchen faucet with pull out sprayer as well as new soap dispenser
Fall pm on 01/02/19 On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter recommended air filter need to replace on time also need UV Lights Install unit operating normal at this time.
Upon arrival I confirmed price with customer and explained the Intellistart so they knew what they were buying. Shut down unit and installed Intellistart. Wired with comfort alert and confirmed wiring with schematic. Returned power to unit and tested. Unit operating normal. Customer mentioned that they donâ€™t feel as comfortable at same temperature after pm service. Found unit operating normal with normal deltas at all components. Found humidifier has too much water flowing thru. Reduced water pressure at piercing valve so pad doesnâ€™t get over saturated and more humidity is produced.
On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections inspected coil,heat exchanger,safeties ,blower,also inspected ductless systems.all units are operating normal
On arrival set unit to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections inspected water pressure and raised it.checked filter ,cap,Contactor,unit is operating normal
I operated the unit on heating mode. I increased manifold pressure from 3.0 to 3.5 iwc. The temperature rise was close to 70 degrees which is at the upper limits for the units heat rise. I calculated cfm and found it to be too low. I increased blower speed to med high from med low. This will bring temperature rise into a more comfortable range and be better for the equipment. Otherwise I checked the rest of the system and found it to be in good working order. Unit operating normal. Customer already received an estimate to replace the humidifier, which was my only recommendation.
Washed out prefilters for customer. Operated the unit on high heat mode. Increased gas pressure to the manifold to 3.5iwc. Then I found temperature rise was too high. Most likely someone lowered the gas pressure to decrease temperature rise instead of calculating cfm and increasing the blower speed. I used dip switches on the board to increase the cfm to 1200 from 850. I checked the electrical wiring and electrical systems, all are within specification. Unit operating normal. I am sending a quote for a replacement humidifier.
I replaced the filter upstairs with one provided. I went to test auxiliary heat first but it would not come on. I found the wiring was incorrect. I fixed this issue and the auxiliary heat came on. I then ran in second stage heating mode. I decreased blower speed to increase delta temperature. I pressurized both ground loops to 65psi. I confirmed proper flow rate on each loop. The package unit had a faulty capacitor which was replaced. I checked the electrical wiring and electrical systems, all are now within specification. Both units are operating normal.
Wayne water furnace pm silver spring Md