Street, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Street, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Street, MD
Upon arrival found both systems cooling. Water pressure at 5-7 psi, pumped up to 55 and settled at 50. No leaks found inside before penetrating wall. Found both run capacitors had failed, recommend replacing. Customer had also made note that zoning doesnâ€™t seem to work well at night. States that hallway thermostat will keep system on and freeze out bedrooms. Checked damper operation and operating normal. Would recommend either recalibrating damper system or leaving bedroom doors open to let cool air to thermostat.
Upon arrival I found Geo system flashing both high and low pressure faults. Reset faults and ran system to find loop pump getting voltage but itâ€™s overheating and overamping, not moving any water. Quoted customer to replace pump and he approved. Replaced pump with new. Purged all air out of system by pumping up loop and opening up burp cavity. Opened remaining valves then ran system. Checked loop pressures and temps. Unit now has 20 degree delta at Evap coil. Unit operating normal at this time.
Upon arrival I went to system and pumped down refrigerant into HeatPump. Once refrigerant was removed from lines and AHU I removed old txv and installed new one. Made sure seals were correct and connection was tight. Pressurized System with 400psi of nitrogen and held. No leaks found. Put sensing bulb into place and removed nitrogen. Vacuumed system down to 500micron and held. No leaks found, vacuum held. Opened up valves and let system pressures stabilize. Returned power to unit and ran ac. Superheat 8, Subcool 9, delta t at Evap 23. Let system satisfy thermostat. Unit operating normal. Customer also asked me to take a look at High fan speeds whenever heat is running for first floor system. Found differential settings were not enabled and aux heat lockout was not enabled either, finally system was setup for finish on high stage heat. Enabled aux heat lockout for 40 degrees. Also removed finish on high stage heat so unit will run more efficiently. Both units are operating normal.
Upon arrival customer mentioned that he doesnâ€™t think top floor ac unit is working and wanted verification if bottom floor unit was working properly. During diagnostics I called for ac for top floor system. Found indoor unit running but outdoor unit now. System tripped on pressure fault. Reset fault and put on gauges to find No Superheat and No Subcooling. Opened up AHU panels and adjusted TXV but Iâ€™m not seeing any difference in refrigerant pressures. TXV needs to be replaced. Then went to main floor system and called for ac. Put gauges on system and checked operation. Found normal Superheat, normal subcool, and normal delta air temps. Unit seems to be operating normally. Need to return to replace top floor txv. Part order form has been uploaded. Office please follow up with customer on return to replace txv.
Changed out thermostat and checked operations . Went through completed operations on AC because costumer has had issues with water damage . Thermostat is operating properly . Had it satisfy twice in heating and twice in AC . System is working properly .
Unit #1, the inverter system began operating on cooling after being reset. The charge was 12oz low but no leaks detected. I cycled the unit several times from test mode and from the thermostat and itâ€™s op normal. The only fault code registered is blower limit, but all dipswitch settings are correct. If problem reoccurs a technician needs to come out when the6 can call tech support. Unit #2 was off at the outdoor unit because of multiple low pressure trips. I went into the attic and found the air handler was set for y1 only which is low cool. I jumpered y1 and y2 so that the blower will move twice the airflow and then checked the charge, unit operating normal. I called service manager to let them know what I had found and done.
Warranty call when arrival customer explained to me what happened customer set point for thermostat 63 *F house temp 70*F unit running nonstop set unit to call for cooling also checked electrical connections checked voltage and amps I cannot find the problem I call tech support for water furnace I over some diagnostic with tech support the problem was the T-stat is bad I gave quote for customer accepted I ordered the parts we have to come back to replace the thermostat unit tested unit operating normal without thermostat problem. Also I have case# 479485 name T-stat-Tpcc32u01. No payment collected.
Completed Ac inspections
Fall pm on 01/07/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters recommended unit #1 capacitor low riding need to be replaced unit operating normal at this time.
Installed the gateway device and paired it to the main levels thermostat. Customer has to finish the setup and registration process. In regards to the airflow, I trimmed the airflow by 10% using the settings in the Comfort Net menu of the thermostat. The outdoor temperature was displayed correctly. The upstairs unit uses a different thermostat that is already connected to WiFi.