Sykesville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Sykesville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Sykesville, MD
Tom - Sykesville, MD
Yonas, did a great job. No complaints at all. Very seldom do I rate anything Excellent. But as I said Yonas did a great job - explained everything he was doing. plus made recommendations on some maintenance item and why
Response from Supreme Air:
Good morning Tom! We appreciate you taking the time to leave an amazing review about your experience with Supreme Air! we look forward to working with you in the future! Thank you for being a Supreme member!
On arrival we checked thermostats. We inspected both of the water furnace(7 series and 5 series). We inspected capacitor, thermostat connections, contractors, LWP,EWP,EWT,and LWT. After finishing with the inspection we waited for the system to start running. Units are operating normal.
I replaced the filter with one provided by the customer. I operated the unit in second stage and auxiliary stage heating mode. I reset blower high speed from 8 to 7 to increase the temperature rise to 25 degrees. I confirmed proper flow rate and adequate loop pressure as well as heat of extraction. I checked the electrical wiring and electrical systems, all are within specification. The unit is operating normal. I am sending the customer an estimate to install a humidifier.
I operated the unit on second and auxiliary heat stages. Increased blower speed in auxiliary heat stage to decrease temperature rise. I confirmed proper flow rate and heat of extraction. Ground loop pressure holding within recommended range. I checked the electrical wiring and electrical systems, all are within specification. Zoning is operating as intended. Unit operating normal.