Sykesville, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Sykesville, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Sykesville, MD
Tom - Sykesville, MD
Yonas, did a great job. No complaints at all. Very seldom do I rate anything Excellent. But as I said Yonas did a great job - explained everything he was doing. plus made recommendations on some maintenance item and why
Response from Supreme Air:
Good morning Tom! We appreciate you taking the time to leave an amazing review about your experience with Supreme Air! we look forward to working with you in the future! Thank you for being a Supreme member!
On arrival set units to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections inspected drain and cleaned it ,inspected water pressures,coils,caps,contactors ,filters .units are operating normal at this time
Installation of Amana Heat Pump System Heat Pump M# ASZ160241 S# 1904298826 Air Handler M# ASPT29B14 S# 1904133604
Spring Pm On 05/31/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter and replaced checked compressor capacitor checked all other electrical connections unit operating normal at this time.
Replace shower diverter with new one.
Install customer supplied vanity and faucet in first floor hall bath customer has vanity picked out and paid for asked us to pick up from Home Depot in randallstown customer will send over info for pickup
Spring Pm On 05/02/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter cleaned checked EWP and LWP also temp checked compressor capacitor I was recommended replacing contactor customer accepted quote replaced the contactor checked electrical connections checked voltage and amps I tested start up and unit began operating very smoothly without any hesitating or lag unit operating normal at this time. Collected $150 balance on CC on file.
Customer gave deposit of $263.92 on 4/22/19 to install vanity faucet is scheduled to arrive on Wednesday 4/24/19 will call to schedule when it arrives
Spring Pm On 04/08/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter is cleaned checked capacitor checked EWP and LWP psi unit tested unit operating normal at this time. Recommended UV lights installation
To replace sump pump and battery back up sump pump system in back sump pit To cut open wall behind the upstairs shower and install a Moen Adler single handle diverter , will also replace drip ear elbow as the shower arm snapped in the elbow customer responsible for all drywal repairs To cut out and repipe kitchen sink and dishwasher drain from the tailpiece to the wye for dishwasher and the trap as well will use fernco to connect to existing pipe To cut out make hole bigger in concrete foundation to install new frost proof hose bibs , one on side 4â€ frostproof , also the front one with an 8-10â€ frostproof hosebib Cut out abs pipe for kitchen drain under sink. Replaced trap also repiped the branch line for dishwasher Replaced hose bib out front and back of house with frostproof hose bib - copper is leaking from old 90 and running down pipe will need to cut out pvc drain for sump and replace the copper 90 then repair the pvc Pulled sump pump system out of pit , installed new rig
Customer paid $1578.00 deposit on work to be done ,would like Thursday to complete work , check did scan will bring to office
Replace 38 gallon electric water heater in basement need install ball valve expansion tank and pan
Need to return to install 36 gallon lowboy electric water heater
On arrival we checked thermostats. We inspected both of the water furnace(7 series and 5 series). We inspected capacitor, thermostat connections, contractors, LWP,EWP,EWT,and LWT. After finishing with the inspection we waited for the system to start running. Units are operating normal.
I replaced the filter with one provided by the customer. I operated the unit in second stage and auxiliary stage heating mode. I reset blower high speed from 8 to 7 to increase the temperature rise to 25 degrees. I confirmed proper flow rate and adequate loop pressure as well as heat of extraction. I checked the electrical wiring and electrical systems, all are within specification. The unit is operating normal. I am sending the customer an estimate to install a humidifier.
I operated the unit on second and auxiliary heat stages. Increased blower speed in auxiliary heat stage to decrease temperature rise. I confirmed proper flow rate and heat of extraction. Ground loop pressure holding within recommended range. I checked the electrical wiring and electrical systems, all are within specification. Zoning is operating as intended. Unit operating normal.