Woodstock, MD Air Conditioning, Heating and Plumbing Services
Supreme Air provides Air Conditioning, Heating and Plumbing Services, Repair, Installation, Maintenance, and Tune Up in Woodstock, MD and surrounding areas.
Check out what some of our customers are saying about Supreme Air.
for Woodstock, MD
Upon arrival added 4 lbs 6 oz to system. System now operating with 325 psi (high) 125 psi (low) 8 degrees of sub cooling, 14 TD on outside coil and 18 TD on inside coil.
Installed bathroom faucet pop up assembly drain valves and escutcheons installed trim kit for shower still need to install slider rod and toilet wall is not painted yet to install toilet also kitchen floor is not finished and cabinets are not installed to complete trim will need to return once painting flooring and cabinets are installed and appliances are here to hook up and test
Customer had no water to home found water service line under trailer not buried but insulated and wrapped with heat tape plug had come loose for heat tape causing line to freeze once heat tape was back on line thawed and water was restored to home
To cut and repair broken cpvc pipe in ceiling Replaced split cpvc line in basement ceiling , customer had another plumber out last night who made the top connection also cpvc is very very brittle from well water and age would highly recommend a repipe at least going up to the kitchen also need to insulate the back wall as there is no insulation up high and itâ€™s noticably freezing cold in the bay.
On arrival found system locked on pressure switch ,I then reset system ,unit came back on,checked pressure ok.checked exhaust motor which was rated for .75 and actual was .8 amps,motor was hot to touch .also pressure switch kept opening ,unit is 15 years .needs pressure switch and exhaust motor. .unit is in bad shape better to replace
No heat on a Miller furnace in Woodstock , Md .